Govt orders probe into fire at Chennai ATC
Chennai/New Delhi: Government on Tuesday ordered a probe by the Directorate General of Civil Aviation into the fire incident at Chennai airport`s Air Traffic Control room in the wee hours.
The fire was caused due to malfunctioning of batteries, Airport Director HS Suresh said in Chennai.
The battery bank area of the ATC tower was engulfed in fire following an explosion in the UPS (uninterruptible power supply) system of the battery bank in the technical equipment room that supplies power to advance surface movement guidance and control system at around 2.20 AM. But there were no casualties.
"An enquiry has been ordered by Ministry of Civil Aviation. DGCA has been directed to conduct the enquiry to identify the cause of the incident and suggest remedial measures and submit a report at the earliest," an official statement issued in New Delhi said.
Flight operations were affected for about seven hours and the ATC system could be fully restored only around 9 AM.
Five international flights arriving at the Chennai airport, between 2.30 AM and 5 AM, had to be diverted to Bangalore and Hyderabad.
Four flights were diverted to Bangalore and one to Hyderabad as part of the contingency plan and standard operating procedures (SOPs) after the officials were forced to vacate at the area control centre due to thick smoke.
During this period, six departures were also delayed which had a cascading effect on 13 more departing flights.
The flames were noticed by the maintenance personnel on duty in the technical equipment room on the third floor of the Air Traffic Services (ATS) complex.
The fire control officials on duty at ATS complex tried to extinguish the fire.
The fire was brought under control by the Airport Fire services personnel at around 2:45 AM after five fire tenders were pressed into service.
As a preventive measure, power supply and airconditioning was switched off as technical and area control centres were engulfed in thick smoke.
It was restored at around 3 AM, after the smoke got cleared. There were no damage to the equipment and the system, the statement said.
More from India
More from World
More from Sports
More from Entertaiment
- Admissions 2015: Know India's best ranking Universities
- Zee Media Exclusive interview with UPSC topper Ira Singhal's family
- UPSC announces Civil Services Examination 2014 results
- Dr Subhash Chandra Show: Is Corporate Social Responsibility nothing but a marketing gimmick?
- Watch: Top 25 Headlines @ 12 pm
- UPSC announces Civil Services Examination 2014 results; women bag top four positions
- 3rd Test, Day 2: Sri Lanka rattle Pakistan in decider
- Indian Mujahideen chief Yasin Bhatkal indicates Islamic State will help him get out of jail soon
- Missing UK schoolgirls seen carrying Kalashnikov rifle in ISIS's Raqqa?
- Met Dawood Ibrahim in London, he wanted to return to India: Ram Jethmalani